pCO xs. User manual. Manual version: dated 14 november program can be used with CAREL pCO1 medium, pCOXS or pCO3 Medium and Large. sistema +EN rel. – IMPORTANT. CAREL bases the development of its products on decades of experience in. HVAC, on the. Manual Control Ad Or Carel pCO Xs – Download as PDF File .pdf), Text File .txt) or read online.
|Genre:||Health and Food|
|Published (Last):||10 June 2015|
|PDF File Size:||16.75 Mb|
|ePub File Size:||16.89 Mb|
|Price:||Free* [*Free Regsitration Required]|
Page 75 Can only be activated on one serial port. By pressing ‘print’ button you will print only current page. Page 3 CAREL, its employees or subsidiaries be liable for any lost earnings or sales, losses of data and information, costs of replacement goods or services, damage to things or people, downtime or any direct, indirect, incidental, actual, punitive, exemplary, For further information on the parameters and on the variables that can be exchanged, see to the pvo manual.
CAREL PCO SERIES USER MANUAL Pdf Download.
Pco 1 Controller pCO Sistema 2. Configuration Of The Plan Network 5. L5 L5 L5 L5: The information to be printed cpo be completely configured in the application. All the supervision and management operations already described for the PSTN protocol can thus be performed.
Don’t have an account?
Comments to this Manuals Your Name. If this is still near zero, turn the controller off and wait a few minutes. Gsm Protocol gsm Modem With WinLoad, the user can completely carrel the unit in a simple and intuitive manner.
When the protocol is set on the FieldBus serial port, the remote WinLoad connection is not possible. Page of 84 Go. Maximum number Type Universal: Got it, continue to print. The inputs must be configured for 0 to 20 mA or 4 to 20 mA signals by the application program resident in flash memory.
Page 20 Maximum careel Type Universal: Page 30 pCO Sistema 3. Can only be activated on one serial port. Page 58 pCO Sistema 8. Page 19 pCO Sistema 2.
Page 28 pCO Sistema 3. These inputs are all optically-isolated from the other terminals and can operate at 24 Vac, 24 Vdc and some at Vac. To print the manual completely, please, download it.
Carel pCO series User Manual
This allows the control of the fundamental parameters of the OEM humidifiers manufactured by CAREL level and conductivity of the water in the cylinder, TAM sensor for current input directly from the pCO electronic microprocessor controller.
Pco 3 Technical Specifications Can be selected via software.
Page 35 pCO Sistema 4. This is also true Selecting this function displays the names of the IUP, Completely wireless carel solution for the management of ambient comfort in buildings 44 pages. Pco 1 Technical Specifications Type Universal: Table of Darel Add to my manuals Add. Today in fact, with the expansion of BMS, the issue of communication between controllers made by different companies is increasingly important.
Otherwise, there must be another possible procedure for selecting the protocol e. Page 37 pCO Sistema 4.
Page 42 pCO Sistema From the logical point of view, the connections are shown in the following figure: