Setpoint. Display. Chromalox® Heil Quaker Boulevard • Lavergne, Tennessee Telephone: • FAX: QuickInfo. The Chromalox 1/4 DIN Temperature and Process Controller is a low cost, high performance single loop controller that can be used for temperature, flow. Find great deals for Chromalox rr RR Temperature Controller. Shop with confidence on eBay!.
|Published (Last):||3 April 2013|
|PDF File Size:||8.25 Mb|
|ePub File Size:||7.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Your shipping cost will be displayed in your shopping cart.
CHROMALOX TECHNICAL MANUAL Pdf Download.
On each PAGE you will find a specific set of related functions. Enter text from picture: The Digital Input can be setup to function as a remote alarm reset button see pages This makes it an exceptional choice for OEMs and distributors with multiple control cromalox, manufacturing facilities, testing facilities and testing applications.
Mounting Dimensions Figure 2. Page 51 Chromalox Technical Manual Section 6 Alarms The controller can provide up to three alarm outputs using Output 3, 4 and 5.
If a failure chroma,ox in the control circuitry of the controller, the control output will be turned off and ERR3 will be displayed on the lower display. To print the manual completely, please, download it.
Page 71 Chromalox Technical Manual Temperature extremes and excessive moisture can damage the instrument. Page 54 Operation cannot be reset until the process is out of the alarm condition. Don’t have an account? Wiring Chromalox Technical Manual Page 4 3-Wire mA, Vdc Transmitter The Chromaloz output is always enabled when the power is on.
The setpoint can be changed in the Normal Display Mode using the pushbuttons, if the Security Level allows setpoint changes see page 26 for Security Levels. Page 82 Sensor maximum ranges are: Millimeters are shown in parentheses. Page 37 Chromalox Technical Manual The CLP Alarm responds to specific conditions that may provide early warning of system loop failures or aid in troubleshooting failures. AC Neutral Load Figure 2.
Chromalox 1/4 DIN Digital Temperature and Process Controller
The has up to seven 7 hardware switches 21104 located on the bottom of the controller. Page 11 When driving a contactor coil or other inductive load, an appropriately rated AC snubber circuit is recommended Chromalox Part. Installation Temperature extremes and excessive moisture can damage the instrument. Loop Alarm Output Output 3, 4, or 5 will be activated if selected.
By pressing ‘print’ button you will print only current page. Output 5 Figure 2.
Hardware Setup RS can be used to connect a computer or modem to a single controller. The CLP is not a substitute for safety shutdown devices such as flow switches or overtemperature monitors.
Chromalox 2104-rr100 2104RR100 Temperature Controller
Loop-Powered Common Figure 8. Chromalox Technical Manual Section 7 Digital Input and AUX Function The controller gives you two different options for actuation of any one of several field-selectable controller functions: Tighten the mounting clip screw do not over- tighten to secure the controller firmly against the mounting surface.
Page of Go.