UDC Controller Manual. Download Link: PDF icon Product Mfg: Honeywell Field Instruments. Figure 1—UDC Controller has a sealed faceplate suitable for hosedown Honeywell’s Windows™-based. LeaderLine PC . Manual mode, failsafe output. View and Download Honeywell UDC product manual online. Universal Digital Controller. UDC Controller pdf manual download.
|Published (Last):||20 September 2009|
|PDF File Size:||2.69 Mb|
|ePub File Size:||6.80 Mb|
|Price:||Free* [*Free Regsitration Required]|
Enabling or disabling Use the procedure in Table to enable the remote setpoint source. They are used to determine the reason for a controller failure. If you select PD with Manual Reset you can also configure the following variations: Procedure 7 Table explains how to troubleshoot janual Keyboard failure.
Operating Two Loops of Control 5. Requires 330 the Input 2 temperature signal be a transmitter type input. The ramping current setpoint can be viewed as SPn in the lower display. Do not run slidewire cable in the same conduit as AC power. Function of keys Table shows each key on the operator interface and defines its function. Set Up group that you have selected.
Honeywell UDC 3300 User Manual
Current output on Loop 2 requires auxiliary output. Start-up Procedure Use Accutune to tune the controller; see the procedure in this section. Page 4 Chassis Ground. Forces loop to manual mode. Procedure 6 Table explains how to troubleshoot Alarm Relay Output failure. Other offers may also be available.
Write the model number into the Time Proportional Output has a resolution of 4. The installation section provides information on protection against electrical noise, connecting external equipment to the controller, and shielding and routing external wiring.
Honeywell UDC User Manual – Page 1 of |
Universal digital honeywdll printed wiring board replacements 8 hineywell. Digital Input Option remote Switching Resets the Setpoint program back to the beginning of the first segment in the program and leaves the program in the same Run yoneywell Hold mode that it was in when the DI closed.
Page If the calculated value of the quantity under the square root sign decreases to a value less than 0. Nx series constant and variable torque variable speed drives for induction motors 86 pages. How to replace the Refer to Figure and follow the procedure listed in Table The setpoint at the time tuning starts is captured and Tune runs until completion, then proceeds to the new SP value following the completion of tuning.
Configuration Check Make sure you: Contact your local sales office for warranty information. See the Section 3 – Configuration for specific instructions to set the lockout. Section 2 — Installation 2.
Action Disabled means that the digital input or digital combination parameter is configured but the action cannot occur when the digital input is active because the selected parameter is disabled. Process retuning occurs as the process dynamics are learned. Hold key down to cycle through configured setpoints. See terms – opens in a new window or tab. RTD inputs Use the copper leads and connect the calibrator to the rear terminals of Input 1 or 2.
As the tests are run, the displays will appear as shown in Table maual REStot Resets the accumulated ,anual value. PV adaptive tuning whenever a PV process disturbance of 0. The lower display will still show Gain.
Accutune can be used on either or both loops. Page 81 0 to x Totalizer Scale Factor. Customer should size fuses accordingly.
HONEYWELL UDC USER MANUAL Pdf Download.
Page – Table Troubleshooting Time Proporti Check the displays and Use the procedure in Table to run the display and key test. The Program selections are: Back to home page.
Page – Table Troubleshooting Position Prop This value allows an alarm setpoint value Configure the values for: Select tuning The procedure in Table shows you how select the Tuning parameters for each Parameters. Refer to eBay Return policy for more details. Configuration Procedure Set Up group that you have selected.
When one loop is operating by PV adaptive tuning, the other loop can have its configuration changed. Use Fast Bio fuses only.
In order to determine what is causing the error: